Section I. Accountability and Inventory. PETROLEUM ACCOUNTING RECORDS AND REPORTS. Soldiers storing or transferring class III products must. provide extensive information about FM ( ). SUPERCESSION STATEMENT. This publication supersedes ATP dated 21 July , FM dated 2 April. and FM
|Country:||Republic of Macedonia|
|Published (Last):||7 December 2014|
|PDF File Size:||3.14 Mb|
|ePub File Size:||4.71 Mb|
|Price:||Free* [*Free Regsitration Required]|
All areas should be attractive and free of fire hazards. Make sure the tape is not lowered so far into the 10-6-1 that the bob tilts and causes an incorrect gage. Sign In Sign Out.
Concepts and Equipment of Petroleum Operations (FM ) by Army, Department of the
Record physical inventories on DA Form use the remarks block for petroleum tank vehicles. Maintenance procedures of the hoselines include the following. The tank car gage stick is made of hardwood or similar material. It must be clean and dry.
Concepts and Equipment of Petroleum Operations (FM 10-67-1)
This is not organizational level maintenance. Use the gage stick as given below.
Hose and hose assemblies, synthetic rubber, reinforced, water- and oil resistant, nonmagnetic and regular service, high-pressure type type C MIL-H ships latest revision. The calibration charts should be checked periodically.
If left unchecked, erosion weakens firewalls so that they are not able to act as 100-67-1 secondary containment for a spill or prevention of a f from spreading to another source. When taking samples, follow the procedures in the ASTM manual and the precautions listed below:. Marine loading arms have a hydraulics system or a set of cables which moves the piping into position.
Temperature measuring procedures are as follows:. A yardstick, along with the graph shown in Figurepagestep B, can be used as a field expedient to determine the approximate number of gallons in a gallon drum.
Hydrometer, graduated scale, API 29 to 41 range mm long, 14mm diameter, with thermometer. Home Contact Us Help Free delivery worldwide.
NSN ITEM Hydrometer, graduated scale, API 9 to 21 range mm long, 14mm diameter, with thermometer Hydrometer, graduated scale, API 19 10–67-1 31 range, mm long, 14mm diameter, 10–67-1 thermometer Hydrometer, graduated scale, API 29 to 41 range mm long, 14mm diameter, with thermometer Hydrometer, graduated scale, API 39 to 51 range mm long, 14mm diameter, with 01-67-1 Hydrometer, graduated scale, API 49 to 61 range mm long, 14mm diameter, with 106-7-1 Hydrometer, graduated scale, API 59 to 71 range mm long, 1 mm diameter, with thermometer Hydrometer, graduated scale, API 69 to 81 range mm long, 14 mm diameter, with diameter Cylinder, ungraduated, mm high, However, they are responsible for maintaining the pipelines, hoses, hose-handling equipment, grounding systems, and mooring devices at waterfront operations.
Make sure it does not rest on a rivet head or other object within the tank. Make sure the tape is lowered to the same depth for both gages. A 5-gallon sample should be submitted when jet fuels are tested for thermal stability. Do not go over PSI unless it can be determined that the hoses were designed by the manufacturer to take more.
Keep it in position for 15 to 30 seconds for heavier products. Contamination 10-67–1 consist of solid foreign matter, free or emulsified water, mixed fuels or grades of fuel, or all of these. This manual is oriented toward tactical field operations and deals with the responsibilities of both management and operator personnel.
Other devices, such as wire ropes, cables, tower timbers, cross braces, and deadman anchors, are used to 10-7-1 pipelines across streams and ravines. Gaging operations requires using special terms.
If any 01-67-1 these things are in the tank in sufficient levels to cause contamination, clean the tank before using it. Calculate the monthly loss by subtracting the closing inventory from the closing book balance. The zero point is the point 1067-1 contact between the snap and the eye of the bob.
Make sure the tape is not lowered so far into the tank that the bob will tilt and cause an incorrect reading. This destroys the grade inside the firewalls so that runoff water flows to the tank instead of from it.
10-67–1 equipment consists of devices such as cranes, slings, hoists, winches, A-frames, and gin poles. The Best Books of Hose assemblies, rubber, oil and gasoline discharge, smooth-bore, lightweight buoyant type MIL-H ships latest revision Hose and hose assemblies, synthetic rubber, reinforced, water- and oil resistant, nonmagnetic and regular service, high-pressure type type C MIL-H ships latest revision Hose and hose assemblies, rubber, oil- and gasoline discharge, smooth-bore, lightweight, buoyant type; reattachable couplings and adapters MIL-H ships latest revision Hose, rubber, gasoline, with reusable couplings, low temperature MIL-H, latest revision.
Also, ships and tankers should be grounded and bonded with a flexible copper cable during fuel transfers. Grades 4, 5, 6, and Navy Special burner fuel oil. As a rule, liquid samples should be 1 gallon and semisolid samples should be 5 pounds. Table gives the minimum number of temperature readings and the measurement levels for various product depths.
A mooring facility is located at the ocean end of submarine pipelines. To maintain them, follow these steps.
Soldiers storing or transferring class III products must accurately account for receipt, issue, and stocks on hand for both bulk and packaged products. It also washes away soil under the tank, causing the tank to settle. Hydrometer, graduated scale, API 19 to rm range, mm long, 14mm diameter, with thermometer.
Estimate as closely as possible the indicated volume when the cut mark falls between divisions. Capacity tables showing quantities of either innage or outage gages should be based on accurate tank calibration data.
The sample types are given below. Do not use ink because ink will run if fuel is spilled on the tag. Marine loading arms Chapter 4 10-671 being used instead of hoses and hose-handling equipment at many waterfront facilities. The types of contamination are given below.